CTX-393sb MultiAction 10 tablets 250g
Multiaction chlorine treatment for pool maintenance
- Slow dissolution and continuous disinfection
- Disinfection, anti-algae, algaestatic, flocculant, coagulant, chlorine stabilizer, anti-lime, metal remover, corrosion protection, pH reduction
Solid compound in tablets, specially formulated to eliminate bacteria, viruses and microorganisms in general, prevent the development of algae and keep the water crystal clear and transparent. In addition, it allows a slower and more homogeneous dissolution of the tablet, avoids disinfectant peaks and reduces its consumption. These tablets leave NO residue, reduce the consumption of other chemicals and reduce water consumption for filter cleaning.
Pure Drop Technology allows a controlled and effective disinfection, without residues on the surface and without boric acid.
In our formula we have managed to completely eliminate boric acid. In Pure Drop Technology we have substituted it, which makes the tablets last 50% longer, maintaining a controlled and constant release of chlorine.
PURE DROP TECHNOLOGY
· Boric acid free
· Lasts 50% longer
· Leaves no residue in the water
|69868||CTX-393sb Multi action 10 4 Kg|
INSTRUCTION FOR USE
Always adjust the pH before adding chlorine to the water to make it as effective as possible.
To introduce the necessary dose of product inside the skimmers, putting then in operation the filtration equipment, in order to be able to dissolve the product when circulating the water through the skimmers.
It is essential that the entire volume of water in the pool is recirculated through the purifying equipment on a daily basis.
The free residual chlorine should be between 0.5 and 2 mg/l, a value that can be easily measured using a chlorine and pH analyzer kit. This control should be carried out at least twice a day.
Treatment Start of season: Add 15 grams of ClorShock per m3 of water. After 2 hours, adjust the pH of the
water to between 7.2 and 7.6 using ctx 10 pH Minus solid or ctx 20 pH Plus solid.
This treatment should be repeated whenever there is a lack of transparency in the water.
Maintenance treatment: With the pH of the water adjusted, add 1 tablet per 30 m3 of water every 7/ 10 days.
These doses are for guidance only and may be modified according to the characteristics of each pool, climate, etc